Hazardous Location Panels
Hazardous location rated panels are the panel which are approved to be installed in Div 1 or Zone 1 and lower divisions or zones. There are various methods of protection which are used to rate the panels or components for this area. We categorized few of the most common ones which we use to rate our panel for the hazardous area. Explosion proof panels use the heavy cast metal enclosures and this method of protection is called flame proof. Hazardous location panels use various methods of protection which can be from intrinsically safe to encapsulation.
Explosion Proof or Flame Proof Panels
Explosion proof motor starter c/w main disconnect, start/stop, running pilot light and overload reset operator. This panel rated for Division 1 and 2
Explosion proof motor starter c/w main disconnect, local off remote operator, This panel is rated for Division 1 and 2 and can be started locally or remotely
Explosion proof motor starter designed and built with special controls so it runs only in one direction even the input phase sequence get changed. Mostly this feature is required for the portable units where the input power source is different always and the motor need to be running in one direction only.
These enclosures are designed so that the hot gases generated during an internal explosion are cooled below the ignition temperature of the surrounding flammable atmosphere as the gases are transmitted through the joints of the enclosure. Any parts which are not rated for hazardous area can be installed in these enclosures and then the assembly becomes rated. There are some exceptions apply, that which parts can't be installed in these enclosures.
Purged or Pressurized Panels
Local operator panel fitted with Z purge which converts the inside of the enclosure from division 2 to non hazardous area so some of the incendive non hazardous approved components are used in the panel and the assembly is approved for class I division 2 area.
Purge Y fitted on a enclosure to convert the inside of the enclosure from division 1 to division 2 so we could use all the division two rated parts which were easily available and the whole panel is approved for class I division 1.
A VFD panel rated for division 2 area. This panel is fitted with Z purge which converts the inside of the enclosure from division 2 to non hazardous area and we could use the VFD controller and all the other non approved incedive components inside this panel. As the VFD controller produce ample amount of heat so we installed a division 2 rated air-conditioner on this panel to cool the inside.
This is type of protection which prevents the entry of the surrounding atmosphere it the enclosure by maintaining positive pressure within the enclosure of a protective gas at the higher pressure than surrounding atmosphere. Purge Types X Changes the area within the unit from Div.1 to nonhazardous Y Changes the area within the unit from Div.1 to Div.2 Z Changes the area within the unit from Div.2 to nonhazardous
Intrinsically Safe Panels
A method of protection based on the limitation of electrical energy to levels where any open spark or thermal effect occurring in equipment or interconnecting wiring that may occur in normal use, or under fault conditions likely to occur in practice, is incapable of causing an ignition. The use of intrinsically safe equipment in a hazardous location also requires that associated wiring and equipment, which is not necessarily located in a hazardous area, be assessed as part of any intrinsically safe system. Generally this is achieved by installing the barriers in the circuits which limits the energy and makes the sparks incapable of igniting the gases.
Hermetically Sealed OR Sealed Device Panels
HMI and other parts used in this panel are rated for Division 2, so the whole assembly is rated for Division 2. This type of design can be lot economical if there has to be lots of operators on the door and time to time there can be changes in the sequence of operation.
Main panel for a distillation skid in hazardous rated for Division 2. This assembly is built using sealed and non incendive devices. Some of the components required for this panel were not rated for area so we sent those to an inspection company for a destructive test and then were approved to be used on this panel.
Local operator panel for a filtration unit rated for Division 2. It was not economically possible to build the main panel rated for Division 2 due to the parts use in the panel. So the main panel was installed in the non hazardous area and the controls required to operate the filtration unit were designed on this small panel and interconnected together in the field.
These are the panels built by using hermetically sealed devices. Any arcing or sparking contacts in these devices are hermetically sealed against the entrance of gases and vapours
Hazloc. Control Stations
Control Station contains potentiometer, selector switch and emergency stop. This is custom made to control a variable frequency drive from Class I Division 1 area.
This control station approved for Class I Div 1 and Zone 1. This is custom built to start and stop a motor from hazardous area remotely.
This control station approved for Class I Div 1 and Zone 1. This is pre-built start stop control station with a pilot light showing the motor run status.
This control station approved for Class I Div 2 area only . This is custom built using operators having sealed contacts and nema 4X stainless steel enclosure.